How to install ceiling mounted dehumidifier for home
? Hangzhou Greeme Environmental Co., Ltd., by researching the machine itself and industry experience, summaries some installation methods. Now we would like to share to customers how to install ceiling mounted dehumidifier for home
. The installation of ceiling mounted dehumidifier for home
should be divided into three parts: the installation of dehumidifier, the connection and installation of air duct and the installation of machine drainage pipe.
I.Installation of dehumidifier
1. Suspender installation
Before installation, the installation position should be determined first. After precise positioning with chalk and measuring tools, the drill is used to drill holes in the determined position, and the expansion screw is punched, the size of which should be not less than M8.
2. Installation of dehumidifier
Before installation of the dehumidifier, four sets of M8 nuts 1, elastic cushion and flat cushion should be installed respectively on the four expansion screw, then the dehumidifier should be moved horizontally upward to penetrate the expansion screw into the lifting lug of the dehumidifier. And then a nut 2 should be rotated separately to install the dehumidifier on the expansion screw. It should be noted that the dehumidifier should not be inverted at any position, otherwise the dehumidifier will be damaged.
3. Horizontal Installation
After the dehumidifier is installed, the fixed nut 2 can be adjusted and tested with a horizontal ruler to make the fuselage reach the level of installation. (In order to ensure that the dehumidifier can discharge water normally and avoid potential leakage hazards). Finally, usethe nut to lock the dehumidifier. The installation of the dehumidifier is finished.
II. Installation of air ducts
1. Installation of air intake pipes
The air intake and fuselage should be as close as possible, while the difference between the air intake and the dehumidifier itself should be as small as possible. The shorter the air intake pipe, the better the dehumidifying effect. The maximum length of the intake duct should not exceed 1.5m. It should be closely connected with the air inlet of the dehumidifier (there should be no obstacles in front of the air inlet).
2. Installation of air outlet pipe
The distance between the air outlet and the fuselage should be as far as possible, but the longest air outlet should not exceed 5 meters. The difference between the air outlet and the dehumidifier itself should be as small as possible, and the air outlet of the dehumidifier should be closely connected (there should be no obstacles in front of the air outlet).
III. Installation of Drainage Pipes
Ceiling mounted dehumidifier for home
should be 5-10 cm higher than the drainage pipeline. The length of drainage hose can be determined according to the actual situation, but make sure that the drainage is smooth. After the installation, it should be easy to maintain and circulate air.
Hangzhou Greeme Environmental Co., Ltd. has always been committed to providing customers with the best quality dehumidifier, humidifier, constant humidifier and other products. We also provide the most detailed product consultation, product configuration and quotation. What’s more, the most perfect after-sales service is provided. Look forward to cooperation with more customers and friends!